• Target Flame detector type : IR3 only (Contact Rezontech, for more details.)
• Operation time : 2.5 hour
• Weight : about 3.2KG
• Dimension : 250mm X 145mm
• Enclosure : Aluminium(Anodizing Process)
• Operation Tep : 0°C~50°C • Storage Tep: -10°C~60°C
1. Connect AC 220V plug of a charger to the receptacle.
2. Fully discharged battery will be required Maximum 24hours recharging for the appropriate operation.
※ Charge enough after usage.(Min. 16 hours)
※ LED Indicator (Red: recharging fault, Green: Fully charged)
2. Press operation switch ON [with appropriate operation, the light will blink]]
3. Direct the brightest part of light toward flame detector.
4. Wait for the Flame Detector's activation.
5. If the flame detector does not work properly, repeat guided step from 1 to 4 listed above within closer distance.
6. Press operation switch('OFF')
※ Cover range and activation time depend on manufacturer and model.
Normally 5 sec activation time is required within 7m test distance.
7. After the usage, please charge TL205.(operation switch must be set off during recharging)
• Charging status of the Test lamp.
• At the front side, the longest operation distance will be generated for the Test lamp.
• Must Keep it clean all the time
• Do not use any charger except one provided by Rezontech.
• Do not use during charging.
• The main power will be shut down when TL305 detects 20V under low voltage and other failure.
• Charging will recover from circuit and battery failure.
등록된 댓글이 없습니다.